Ask a Question
Can I cable a 3-wire PNP type detector in the interrupt loop of the time delay Y39-Y40 of the XPSAV?
The principle of monitoring the input loops of the Preventa XPSAVxx module with a pulsed voltage makes it impossible to insert PNP or NPN sensors in these loops.
The loops concerned are:
Y39-Y40: time delay interrupt loop
S21-S22: channel 1
S31-S32: channel 2
Was this helpful?
What can we do to improve the information ?
Not the FAQ you were looking for? Click here for a new search