Ask a Question
Why does the display light of Micrologic 6.2 trip unit of Compact NSX not glow even when the load reading is displayed.
Unlike other range of Micrologic the backlighting or display light of Micrologic 6.2 is not self powered by the primary current.
A separate external 24VDC power supply is required for the working of the backlight of Micrologic 6.2. For this, 24VDC power supply connector (LV434210) has to be used.
Was this helpful?
What can we do to improve the information ?
Not the FAQ you were looking for? Click here for a new search