Ask a Question
How to size the Generator or Transformer required for supplying single unit of Drive
The size of the Generator/Transformer should be 1.5 to 2 times the power in VA to that of the drive that is to be supplied.
The Power rating in KVA of a 250KW Drive is 292.2KVA (Reference - Catalogue of Altivar 71). The Generator/Transformer power size in this case will be 292.2 KVA x 2 = 584.4 KVA.
Was this helpful?
What can we do to improve the information ?
Not the FAQ you were looking for? Click here for a new search